Fairview Heating & Air has provided air conditioning, heating, and home performance services to the residents of Antioch, CA and the surrounding areas since 1988.
Call us now at: 925-625-4963 or check out the reviews and testimonials from your neighbors, which make us one of the top rated service provider in Antioch CA.
for Antioch, CA
Our Reviews by City
Great service, even though busy season, our service tech. came within an hour of our call. Very polite and knowledgeable about the problem.
Mr Silva - Antioch, CA
On Time, Completely Trustworthy.
Mr Donald - Antioch, CA
Mr. Robert Conner was prompt, professional and extremely knowledgeable about the equipment and the needed repairs. I found him to be very trustworthy and felt comfortable with his recommendations. He explained everything.I would hire him again.
Great customer service
Mrs - Antioch, CA
Robert knew what he was doing, did the job and was done in a timely manner.
He checked out my air-conditioning unit tell me that it was bad and gave me options of how to fix the problem
mr ray - Antioch, CA
Mr Galvan - Antioch, CA
Fairview came the next day I called for service. Repairs were done in a reasonable amount of time. Repairman showed up on time as promised.
The service was great, the tech was very well prepared to fix the problem and knew exactly what the problem was plus saved me a lot of money em
Lee Ann - Antioch, CA
I would recommend your services to family and friends
Great, honest service - highly recommended
Mae - Antioch, CA
Robert came and explained what needed to be done with our AC unit. Figured out the problem, came up with a solution and was in and out in about an hour. Very satisfied with his service and would absolutely use Fairview Heating again in the future!
Able to come quickly to help us when we were C
Mrs - Antioch, CA
Joan - Antioch, CA
Robert was prompt, friendly and respectful of my home. He is a great technician and a positive representative of your company. Thank you.
Good service, considerate professional.
judy - Antioch, CA
service tech was pleasant and very well versed
gilbert - Antioch, CA
my opinion is that Fairview is a reliable , no nonsense company .
prompt, curteous and genuine service rep
katherine - Antioch, CA
Annual furnace tune up service.
arlan - Antioch, CA
Could not ask for better service. Been doing business for over 30 years with Fairview.
Richard - Antioch, CA
Timely and well done.
Excellent Service, Professional Tech
Mike - Antioch, CA
Robert was prompt, professional, courteous and knew what he was doing. Very please with this service call. Turns out I needed some freon but everything else is okay
Fast and efficeint service.
Mr. Rick - Antioch, CA
Called and asked if he could come an hour prior to 4 hour window. Very friendly, professional and effcient.
Working on a carrier furnace that had a bad control board I replaced it with a new OEM control after getting approval from homeowner since they didn't want to replace the furnace at this time
Here to help the guys install another one of our American Pride series furnace and air conditioning systems that has a 10-year parts and labor warranty along with our one-year satisfaction or your money back guarantee
Found furnace had no gas. traced problem to a tripped earthquake valve at the gas meter. I reset the valve then started and tested heater thru 2 cycles, I also cleaned the flame sensor due to it was starting to build up carbon on it
Sitting up the install date for another one of our new American Pride series HVAC systems
Working on a Ruud furnace found that the thermostat was not working correctly so we replaced it with a new Honeywell T6 series Pro thermostat
Working on a Carrier heat pump that they said was not heating this morning found it operating correctly but when we are down to freezing temperatures outside it has no supplemental heat strips so it can't keep up when it needs to go into defrost mode
Working on a carrier furnace that was not heating that had a bad 3 wire pilot assembly
Just signing the contract to install one of our high efficiency American Pride HVAC systems it's made right here in the United States
Replace control board on a carrier furnace that the fan was running continuously and would not shut off
I tested the Carrier AC and found that the made-in-china duel capacitor Had failed, I installed a new American-made capacitor that has a 5 year warranty in order to start the AC and test it. I then found the compressor would not start it was in locked rotor so I had to install a hard start kit, once it started the compressor ran fine the refrigerant charge and amperage draws are all good overall condition of outdoor unit is fair do to dogs have been peeing on it in the past
Working on a carrier Air Conditioner that was not cooling enough I found it low on freon with a leak at the service valve I repaired the leak and recharge the unit
Working on a Coleman furnace that the fan was not running in AC mode traced problem to the selector switch for the blower speed I bypassed the switch since it was unneeded due to there was only one speed on this furnace started and tested AC no other issues noted at this time other than system is very dirty so homeowner has signed up for our maintenance agreement plan for us to come take care of it clean it and replace the filters peach season
found downstairs fan was not running on the Rheem heater and air conditioning mode trace the problem to a failed control board replace the board after getting approval from home owner with new Honeywell board started and tested system no other issues noted at this time other than system is a 1998 model
On another estimate to replace an old Lennox System where are new American Pride assembled in America system
upon starting the Carrier air conditioning system I found that the indoor blower motor was just humming I traced the problem to a failed capacitor I replace the capacitor with a new American-made one that has a 5 year Parts warranty then restarted system and tested indoor blower motor is dragging and very noisy but is operating at this time and will possibly need replacement in the near future
Replace indoor blower motor on a rooftop Rheem package unit original complaint was burnt smell coming from vents
found the Dual capacitor in a carrier Air Conditioner under warranty was bad replaced with new capacitor started and tested no other issues noted at this time
found Carrier Air Conditioner was iced up I remove the air filters from the grills and checked the furnace there were none in it I then ran the heat for a few minutes to thaw all the ice out and then started the air conditioner found out it was severely low on freon I did a quick check of the outdoor unit where animals have been urinating on it in the past and located a leak in the condensing unit this is an R22 unit and will need to be replaced with a new 410a indoor and outdoor AC unit
tested operation of Rheem heat pump found refrigerant charge was good amp draws were good capacitor was within limits but disconnect fuse block was getting very hot the copper lugs are starting to change color even though all wires were tight system was running at 16 amps total and it's a 60 amp disconnect at this time it will need to be replaced
on a Trane air conditioning system that was not cooling found the safety drain overflow switch was stuck open I cleaned out the drain P-trap and reinstalled the switch started and tested air conditioner found that it was slightly low on R22 freon I recharged it to factory superheat specs no other issues noted at this time
Air conditioning system service and maintenance
Working on a leak detection on a new Payne air conditioner system installed by another company last year found two different leaks at the welds that they had performed we will need to recover remaining freon then properly weld the system evacuate it and then recharge it
found the thermostat wire for the fan from the thermostat was not connected at the furnace control board in the furnace that had been replaced by some other company last winter I reconnected to wire started in tested AC unit and indoor fan everything is running properly at this time I do recommend replacing the AC contactor it is very badly pitted replaced contactor after getting approval on price from homeowner started and tested no other issues with the air conditioner found at this time
replaced air filter in furnace with new filter everything inside the furnace looked clean just a light coating of dust started AC to test it found Chinese made dual capacitor was blown I replaced it with an American-made part in order to test operation Carrier air conditioner is now working correctly with no other issues at this time