Fairview Heating & Air has provided air conditioning, heating, and home performance services to the residents of Brentwood, CA and the surrounding areas since 1988.
Call us now at: 925-625-4963 or check out the reviews and testimonials from your neighbors, which make us one of the top rated service provider in Brentwood CA.
for Brentwood, CA
Our Reviews by City
Mr. Daryl - Brentwood, CA
After contacting Fairview to help us with a previous company complaint, Robert responded promptly and solved our problem to our satisfaction.
One expensive A/C capacitor
Wendy C. - Brentwood, CA
We had our A/C serviced back in June. Based on our experience, we feel that the company charges wayyyyy too much for replacement part. A US-made dual-run A/C capacitor usually can cost up to $40 bucks but yet they had charged us 10X more. We will definitely consider other HVAC shops for future A/C service.
Excellent efficient service
Sarah - Brentwood, CA
Thank you Fairview for the quick response time. Robert was polite and efficient in making the necessary repairs.
Great Service, Knows the Craft
Mr Fore - Brentwood, CA
Tech did an excellent job of knowing the problem and repairing without wasting time... He has my vote of confidence...👍🏻👍🏻👍🏻👍🏻
Great Service, Fast and Efficient
Jerry - Brentwood, CA
Robert actually came two days early as he had time between appointments. It was 105 degrees when he pulled up and gave me a lot of useful info about my air conditioning system.
Great service at a fair price.
Richmond - Brentwood, CA
Robert was very informative as he tested and replace a couple of out of spec parts.
Wendy - Brentwood, CA
Very happy with the service. The technicians troubleshooted the problem and fixed it. I appreciate the fact that they explained to me what the problem was and how they fixed it. Nice!
Fast and friendly
Daniel - Brentwood, CA
I was able to have someone come out a day early since they had an opening in their schedule. Robert showed up and was friendly and personable. My issue turned out to be a simple one, but Robert still did the due diligence to double check everything and answer a couple questions I had. Will definitely use them again!
Excellent from start to finish!!!
Joyce - Brentwood, CA
Heater is working!!
Greg Olson - Brentwood, CA
Very professional and was able to go get control board same day to get it working.
Great Service Awesome Price and Very Nice.
Mrs Marlene - Brentwood, CA
We had wonderful Service, he explained everything which was very appreciated, very professional. Thank you so much.
Great job !!
Mrs Janet Garcia - Brentwood, CA
Will use again thank you for your prompt service
Mr Goodman - Brentwood, CA
Mrs Betty - Brentwood, CA
Leslie - Brentwood, CA
He did great.
Mrs Carolyn Forlow - Brentwood, CA
great polite timely service for a reasonable price!
Mrs Anne Blackmore - Brentwood, CA
Bauer - Brentwood, CA
Very efficient and on time. Great price
Mr John P - Brentwood, CA
Mr Michael - Brentwood, CA
Robert the Tech was very PROFESSIONAL
Very efficient and knowledgeable
BARBARA - Brentwood, CA
Grant was very professional and I felt he was not going to charge me for something I did not need.
chris - Brentwood, CA
Professional service at a good price
dawn - Brentwood, CA
The technician arrived on time and was professional. He did a good job of answering questions and providing information. The price was reasonable and I would recommend this company to others.
Great service still need a copy of bill to submit for refund
RICHARD - Brentwood, CA
tucker - Brentwood, CA
the service was great, clean and efficient. parts where charged at a very very very inflated price and I'm hoping they will correct that pricing. but in fairness to them I did agree to the price for a total before I began checking parts pricing
Looking at replacing a few Bard units
Working on a carrier furnace that had a bad pressure switch
Working on a Lennix furnace that was shutting the burners down due to a dirty flame sensor
Looking at replacing our York system was one of our new American pride systems that assembled here in the USA
Working on a Trane American Standard furnace it was tripped off on error code due to the variable speed motor was not running found it was very dirty and had the insulation from the inside the furnace sucked onto the motor after I remove this and cleaned it unit was running fine
Working on a Carrier furnace that won't heat found it had a bad pilot switch
Working on a Carrier Air Conditioner that was not running traced the problem to a disconnected common wire that turns the AC on
Working on a carrier unit had a field control board and was not starting the indoor fan
Trance furnace inspection
working on a carrier furnace founded headache code 31 which was an open limit switch traced the problem to a field control board that was not turning on the blower I replaced the control board with a new OEM carrier part after getting approval from homeowner I then started and tested the Heat through 3 cycle no other issues to note at this time on the furnace
Working on a York furnace that had a bad pressure switch
Rewired Zone control board and tested operation of heat on a carrier furnace also found the bypass damper was installed incorrectly and is continually open
Looking at a site 2install one of our Daikin ductless mini splits
Installed new Emerson easy reader thermostat for a customer here in Somerset
Working on a carrier furnace that was not heating found that it had a bad control board I replaced it with a new carrier control board started and tested
returned and installed new Carrier blower wheel and American-made General Electric blower motor an American made run capacitor started and tested in heat mode and fan mode from both thermostats heater is working correctly now with no other issues noted
Working on a Williams wall furnace it was not heating do to tripped off safety switch
Working on a carrier furnace that was not heating traced problem to a faulty ignition system
Replacing the inducer assembly on a York high-efficiency furnace
performed seasonal maintenance and safety check on a Rheem furnace washed the air filter ohmed out the hot surface ignitor checked the capacitor for the blower motor checked the flame sensor started and tested heat light off is good along with the amp draws of the inducer and blower motor temperature rise is within factory specs furnace is running correctly at this time
working on a Rheem air conditioner found dual capacitor with reading below the 6% allowed I replaced it with a new American-made part after getting approval from home owner the new part has a five-year warranty on it also rinsed off the condenser coil started and tested A/C no other issues noted at this time
performed seasonal maintenance on a Trane heater washed the air filters cleaned the flame sensor replaced the batteries in the thermostat wiped burner compartment down started and tested amp draws of blower motor and inducer motor are OK even though inducer is a little high heat rise is within factory specs no other issues noted and furnace is running correctly at this time
Installing a new refrigeration unit for a wine room in one of the custom homes here in trilogy
Fall furnace maintnence
found condensate drain was plugged up, I cut the pipe and cleared with nitrogen, and then installed new fittings between coil and pipe