Fairview Heating & Air has provided air conditioning, heating, and home performance services to the residents of Oakley, CA and the surrounding areas since 1988.
Call us now at: 925-625-4963 or check out the reviews and testimonials from your neighbors, which make us one of the top rated service provider in Oakley CA.
for Oakley, CA
Our Reviews by City
Dick Leonard - Oakley, CA
Heater was checked and repaired with in 2 hours from my call for service!!
Grateful for the quick and precise service
Mrs Freer - Oakley, CA
My AC was down right during a heat wave. I called on a Saturday not expecting to hear from anyone til Monday. Got a call Sun afternoon with an appointment between 7:00AM and noon. Problem was quickly found and they had the new part on the truck.
Stefanie - Oakley, CA
Same day service and he had all the parts I needed in his truck. AC up and running in about 30min. I would definitely recommend your company! Thank you again!
Mrs Cyndi - Oakley, CA
My service person arrived on time...in fact a couple days earlier than I had scheduled as they called with an opening. He diagnosed the problem within a minute, solved it and had me up and running within 20 minutes. He was honest and knowledgeable. A little costly but well worth it!
Such a relief
Amelia - Oakley, CA
Our A/C unit was not working, we had the home warranty company send someone out we got charged $75 for the service call, they gave us an estimate of $1000 to repair and stated it wasn't covered under the warranty. Robert came out for a free estimate, fixed the unit on the spot in about 20 minutes and gave us a very fair deal!!! I could not be more happy with the excellent service from making the appointment, him showing up on time, very friendly and knowledgeable, showed me exactly what was wrong, made sure I understood, and showed me how he fixed it. Appreciate the transparency!! Thank you again Robert!!!
Perfect service, feel-good price!
Philip - Oakley, CA
Timing was perfect! Robert was friendly and explained our problem well! Installation and suggestions were great! Will have them come out for any future problems!!
pamelasouza - Oakley, CA
I was beyond happy that he was able to fit me into the schedule on the same day I called and was able to fix my unit in under 30 minutes
Mrs Julie - Oakley, CA
Have used their services and I am always pleased!!!
Fast Response, Great Job, Great Price
Mr Richard Ng - Oakley, CA
Bob fit us in right away the very day we called. He got right to the cause of the problem and has us fixed in no time.
Dianna - Oakley, CA
100 degree weather and my AC broke down on sunday night. I called monday morning and had an appt between 9:30 and 11am. Robert showed up at 9:30 and diagnosed the problem and replaced the fan motor and capacitor under an hour. Happy days again!!
Quick response to my emergency
Mrs sharon - Oakley, CA
Good job, great service
Gabrielle - Oakley, CA
Came out quickly, was very professional, and helpful. Will definitely refer you guys to anyone I hear needs repairs or maintenance!
Great service & price
Mr Jack - Oakley, CA
Robert was great & he knows the AC business !!
Robert is amazing!!! Fantastic service and very informative.
Matthew Vielbaum - Oakley, CA
So HAPPY with the GREAT customer service we received!! Fast and friendly! We will be customers for a very long time!!! THANK YOU VERY MUCH Robert!!
Relliable Value as always
Rosemary - Oakley, CA
Technician was ezcellent - personable and efficient
joyce - Oakley, CA
mr - Oakley, CA
Superior service, great price
Darrell - Oakley, CA
Mr. Robert Conner, is the BEST, not only did he repair my AC unit in less than an hour, he took the time to educate me on why the motor installed by a competitor two years ago failed.Not only would I use Fairview Air again, I will recommend them to my friends.
Mr John Nielson - Oakley, CA
arrived in the time frame promised. Quickly diagnosed the problem. Explained it to me in detail so I understood. Fixed it, tested it.
Very professional and great service.
dabs58 - Oakley, CA
I definitely would recommend Fairview Heating to my neighbors.
Great Service at cheaper than other companies in the area
B Wilson - Oakley, CA
They had a lower service fee than a couple other companies I called in the area and they were able to get someone out the same day when others couldn't. He knew what the problem was right away and got me up and running again quickly!
Excellent service, Fast and Friendly Tech.
Ted - Oakley, CA
Very pleased with the service and would recommend to others.Excellent service and reasonable cost. The Tech that handled our repair was very skilled and also has excellent customer service skills.. Thank you for your prompt service because due to my wife's arthritis we needed heat in our home as soon as possible.
lori - Oakley, CA
eric - Oakley, CA
Great customer service
Jerry - Oakley, CA
Working on a Carrier furnace. Found the condensate trap was plugged up. Removed the trap and flushed with water, reinstalled the trap then started and tested furnace
Working on a day and night rooftop package unit that's not heating in the rain I found someone had cut a hole in the top of it to install the wrong kind of fan motor that allowed water into the unit and on to the control board
Working on a carrier furnace that was not lighting I found that had a faulty 3 wire pilot switch I replaced it with a new part after getting approval from home owner and ran it through three Cycles
Working on a Maytag furnace that was not heating found that it had a dirty flame sensor so it was shutting the burners back down and would not heat clean flame sensor started and tested furnace is not working correctly
installed new duel pressure switch on a York Furnace started and tested through three Cycles no other issues noted at this time heater is working correctly I also reattached the control board that somebody had taken loose inside the furnace
Working on it day and night furnace that was not heating found it has a bad ignitor and an inducer motor that is going bad
Working on a York Furnace it was not heating found that no maintenances have been done to it and the flame sensor was very dirty so it would not keep the burners on
Working on a carrier furnace that was not heating traced the problem to a faulty thermostat replaced it with a new touch screen model that can be operated buy your phone
How to replace a control board in a carrier furnace that was malfunctioning
Working on a Coleman mobile home furnace that the pilot will not stay lit after repairs furnace is now working correctly
tested air conditioner and Heating could not locate any problems with new thermostat this house does have an air cycler system so that it pulls outdoor air in order to pump it into the house I do not know what the parameters or settings are for that controller at this time unit is pulling unfiltered outdoor air everytime it comes on and also has no filter in your return in the master bedroom. blower wheel and housing are very dirty system could use a thorough cleaning
found Payne air conditioner was not running the made in China Dual capacitor has gone bad and the condenser fan motor has also gone bad the windings are open on it and the housing is cool but you can see where it has got extremely hot and has completely melted the label on the side of the motor
found no power to the thermostats went into attic and found main fuse was blown for the furnace replaced it with a new fuse started and tested amperage draw of blower motor was within limits and old fuse was tight could not locate any causes other than the fuse had gotten hot
started and tested Carrier Air Conditioner found compressor side of the made in Mexico duel capacitor had failed and the fan side was reading @ 2.7 when it should be 5 I replaced it with a new American-made part that has 5 year warranty after getting approval from the homeowner started in tested amperage draws and refrigerant was good I also checked the second system but found no issues with it Both systems are running correctly at this time
found indoor capacitor only reading 1.7 and was rated at 10 I replaced it with a new American made part started and tested motor was running with in Factory amps and then performed the semi annual fall maintenance on the heater washed the air filter check the ohms of the hot surface ignitor check the flame sensor and then started and tested Heat no issues noted with any other items
working on a Carrier Air Conditioner that was not running found made in Mexico dual capacitor has failed I replaced it with the new American made capacitor that has the 5-year full warranty on it after getting approval from the homeowner started and tested AC no other issues noted at this time of the operation of AC
found oil leaking out of the control panel of the Payne unit opened Panel and found the made in Mexico dual capacitor has blown completely apart I removed it and installed a new made in America part in order to test the system it does run correctly but will need the new capacitor installed after getting approval from home owner I installed the part permanently there were no other issues noted with this unit the amp draws of the motor and compressor along with refrigerant charge is good
per homeowner thermostat was not responding correctly I found the batteries were dead and corroded in it I wiped the terminals and tried to dump the loose corrosion out of the thermostat I replace the batteries with homeowner provided then reinstalled it but I still could not get it to respond to the installer configuration mode so this thermostat maybe going bad or just needs to recharge itself started in tested air conditioner so that part of it is functioning correctly
working on a Carrier Air Conditioner found air filter was plugged up solid I cleaned and reinstalled had homeowner open up all Supply registers inside house started and tested unit outside found that the compressor needed a hard start kit and was also low on freon with a visible leak at the lower part of the aluminum condenser coil that is non-repairable I recharge system - 10 degrees of subcooling but compressor is drawing mid amps but condenser fan motor is very loud
working on a Carrier Air Conditioner that was not cooling found that the Dual capacitor has blown I replaced it with a new American-made part that has A5 year warranty from the manufacturer and I also had to add a hard start assist I got the compressor to start and I checked the operation refrigerant charge is good and amperage draws were good the only other item that is in poor condition was the contactor other than that air conditioner is running good
found both fuses we're blown in a York heat pump causing it not to run I checked all wiring connections all were good and tight the fuse block in to disconnect the copper is changing colors which means that it has been getting hot I replaced both fuses started and tested unit is running about 10% below Max Amps with no issues noted other than one of the fuses was an incorrect type
started and tested Carrier air conditioning unit could not find any issues with it capacitor was within limits refrigerant charge was at 10 degrees subcooling Factory is 11 so it was within three degrees amperage draw of compressor was below Factory Max Amps and condenser fan motor was right at Max Amps
working on a Coleman air conditioner that is made by York that was not running most of the time over the weekend traced the problem to the compressor and the unit is running near Max Amps and when into locked rotor when I try to start it I added a large hard start kit to it and started and tested unit