Fairview Heating & Air has provided air conditioning, heating, and home performance services to the residents of Discovery Bay, CA and the surrounding areas since 1988.
Call us now at: 925-625-4963 or check out the reviews and testimonials from your neighbors, which make us one of the top rated service provider in Discovery Bay CA.
for Discovery Bay, CA
Our Reviews by City
Good, efficient service
Larry - Discovery Bay, CA
Robert responded quickly, on time and obviously knew his business well. He quickly repaired our heater. He was very professional, friendly and carefully explained the problem and his actions to repair it. I would recommend Fairview.
Great service, very professional!
Judy - Discovery Bay, CA
I have & will recommend Fairview to all my family & friends. They were the most professional and had the best deal of all the places we checked which is why we chose them to replace our system in April. The free maintenance checks the year after are another plus. Robert was professional, friendly, and took care of the service call in a timely manner.
Mr matt - Discovery Bay, CA
showed up on time...courteous and professional.
Great service experience.
Barbara Riggio - Discovery Bay, CA
Robert answered all of many questions. I will be dealing with him for the product I bought.
Long time customer
Mr Rimple - Discovery Bay, CA
Honest, Explained everything
Excellent Customer Service
Mr. Edgar - Discovery Bay, CA
Robert was excellent. Knew the problem right away, got the parts, reasonable price, got job done.
the service was beyond excellent, the price was no bargain but i didnt expect it to be. you get what tou pay for and in this case i assuredly did. n
Mrwalter - Discovery Bay, CA
with who? I'll tell my son who lives in Discovery Bay and anyone else I encounter who might need your services.
Preventive Maintenance Check-Up
Lisa - Discovery Bay, CA
Excellent, convenient and professional service.
Man knew his stuff!
robert - Discovery Bay, CA
Great service and price.
richard - Discovery Bay, CA
claudia - Discovery Bay, CA
Polite service person.
Mr Bill - Discovery Bay, CA
MrChris - Discovery Bay, CA
Our technician was great. He was well skilled open and honest. A little pricey but I appreciate the service
mr walt cummings - Discovery Bay, CA
excellent, but why twice. the free coffee mug had a mail in survey i completed. timely, knowledgeable and courteous. what else can i say?
Working on a carrier furnace that had a trip to limit possibly do to a bad inducer motor
Add to replace an upper limit switch the head failed on a Goodman furnace after PG&E had a power failure
Giving a free estimate on replacing a York HVAC system with one of our new American Pride systems
Installing one of our new American Pride series furnace and air conditioning systems
Working on a York Furnace that the voltage regulator had failed I replaced it with a new part and started and tested
Working on a Rheem furnace that the door switch has gone bad replaced it with a new Factory parts no other problems noted
Out here on a custom home giving a free estimate to install one of our new American Pride series air conditioning systems the high efficiency models in order to get the BayRen energy upgrade California rebates
Performed our fall maintenance that comes no charge for the first year on all of our American Pride series equipment installs Filter was clean flame sensor was clean capacitor was at exact rating started and tested heat amp draws for blower motor and inducer motor we're good temperature rise for system was good Furnace is running great
Installing another one of our American Pride series furnace and air conditioning systems that come with a 10-year parts and labor warranty We are replacing and old York System, the new system is a 18 Seer two stage with a 98% efficient furnace so they should see substantial savings on their energy bills
installed homeowner provided Honeywell thermostat started and tested system thermostat is working correctly now instructed homeowner on how to replace batteries when needed
started and tested Goodman air conditioner found it was frosting over so I turned on the heater to de-ice it and then found it was low on refrigerant only had 1.4 degrees of subcooling 60 PSI on the suction side one of the plastic access caps was cracked and leaking refrigerant in a slight amount
Working on a heil air conditioner the complaint was makes noise after a couple hours of running found that the condenser fan motor had lost the seal and was losing the oil out of it I oiled it after giving the homeowner the choice of oiling or replacement
Looking at an older Rheem HVAC system that needs our free replacement quote for our American Pride Series furnace and Air conditioning system
Air conditioning system service and maintenance
Goodman Ac inspection
Rheem heater repair
Working on a Coleman furnace that was locked out on high limit trip due to no air filters in the system the homeowner thinks it was approximately four years ago that they took it out
In Discovery Bay California working on a carrier furnace that was not heating found carrier furnace was running fan only continuously traced problem to tripped limit switch above burners that is you being used as a roll out switch i reset it, started and tested the heater through three cycles found no issues at all with the flame light off or burner patterns
In Discovery Bay California working on a carrier Air conditioner that was not running found someone had replaced the dual capacitor with a Chinese made part that has already failed we replaced it with a new American made part and started and tested unit
Working on a hile air conditioner and Discovery Bay California found out it was low on refrigerant inform the homeowner home owner of this and they have elected to replace the system with a new higher efficiency furnace and air conditioner
In Discovery Bay California on a no cooling call Opened Carrier AC unit and found a Capacitor was blown on compressor side fan motor had been replaced previously and it has its own capacitor replaced with new American made part that has a 5 year parts warranty after getting approval from homeowner on repair tested unit no other issues noted at this time
In Discovery Bay California working on a tempstar air conditioner there was not cooling found the capacitor had blown a terminal out of it for the start winding of the compressor replace the wire and capacitor started and tested freon levels AC is running with a 19. 8 degree delta T and 16 degrees of superheat
In Discovery Bay in Contra Costa County on an estimate for a new carrier air conditioning system to replace existing carrier AC unit that is not working